The client wanted to see the following in this building:
Space at the site was scarce. We needed to provide a package that took up the least amount of space while delivering the maximum amount of kW output at a set budget. Plus, we needed to provide a system that could be increased by 40% for future growth considerations. Adding another full-size unit on either side of the building. We designed a building package that could be completely assembled and tested in our projects facility, then split for shipping and reassembled at site. This included the roof sections to be completely built and simply dropped onto the building once in place at site.
The split building option created another problem with how we could build the switch gear. Each split only allowed us to max out the width at 14.5’ because of the route to site and our switch gear was 21’ wide. We solved this by stacking the switch gear back to back; controls in the front and distribution breakers in the back feeding the step up, medium voltage, transformers.